Online from: 1954
Subject Area: Mechanical & Materials Engineering
|Title:||Silica in boiler water|
|Author(s):||P. Ghosh, (National Metallurgical Laboratory, Council of Scientific & Industrial Research, Jamshedpur-831 007, India)|
|Citation:||P. Ghosh, (1988) "Silica in boiler water", Anti-Corrosion Methods and Materials, Vol. 35 Iss: 10, pp.8 - 14|
|Article type:||General review|
|DOI:||10.1108/eb020697 (Permanent URL)|
|Publisher:||MCB UP Ltd|
|Abstract:||Steam contamination (solid particles in the superheated steam) comes from the boiler water largely in the carry-over of water droplets. The need for extreme purity of steam for use in high pressure turbines has prompted the development of highly satisfactory devices for separating steam and water in a boiler drum. Consequently, steam contamination has been steadily reduced. Troublesome turbine blade deposits may occur with surprisingly low (0.6 ppm) total solids contamination in steam. In the 3.5–6 MPa range, however these deposits are usually water soluble and can be removed by periodic washing. In the 4 to 10 MPa range, however, silica deposits predominate and these deposits are not easily removed by water washing. With operating pressure of 13 MPa and above insoluble deposits do occur which may be controlled by residual water washing. Before the unit is returned to service, the deposits should be removed by air or water-driven turbine cleaners or by chemical cleaning.|
Articles that form part of the Emerald Backfiles have been created through digital scanning. Whilst all efforts have been made to ensure accuracy, Emerald will not be held responsible for any inaccuracies. If you require further clarification please contact firstname.lastname@example.org.
Existing customers: login
to access this document
Downloadable; Printable; Owned
HTML, PDF (786kb)
Due to our platform migration, pay-per-view is temporarily unavailable.
To purchase this item please login or register.
Complete and print this form to request this document from your librarian